# E.m.f Equation of Transformer Suppose , N1 = No. of turns of primary coil &

N2 = No. of turns of secondary coil of a transformer.

Φm = Maximum flux in core ( webers)

= Bm x A

f= frequency of alternating current in Hz

From the figure , it has been seen that the flux Φ increases from its zero value to maximum value Φm in one quarter of the cycle i.e in 1/4 f second =4 f Φm Wb/s or volt

Now, rate of change of flux per turn means induced e.m.f in volts.

∴ average e.m.f/ turn = 4 f Φm volt

If the magnitude of flux Φ varies sinusoidally, then the r.m.s value of induced e.m.f is obtained by multiplying the average value with from factor. ∴ r.m.s value of e.m.f./turn = 1.11 x 4fΦm = 4.44 fΦm volt

Now, r.m.s value of the induced e.m.f in the primary winding

∴ E1 = (induced e.m.f/turn) x No. of primary turns

∴ E1 = 4.44 f Φm N1 (As Φm = Bm x A )

E1 = 4.44 f N1Bm A .....................(i)

Similarly, r.m.s value of the e.m.f. induced in secondary is,

∴ E2 = (induced e.m.f/turn) x No. of Secondary turns

= 4.44 f Φm N2 (As Φm = Bm x A )

E2 = 4.44 f N2 Bm A .....................(ii)

It is seen from equation (i) and (ii) that E1 / N1 = E2 / N2 = 4.44 f Φm .

from the above equation it is seen that the e.m.f/ turn is the same in both primary and secondary windings.

.

Voltage Transformation Ratio :-

.

From equation (i) and (ii) ,we get

E1 / N1 = E2 / N2 = 4.44 f Φm = K

Constant K is known as voltage transformation ratio.

i) If N2 > N1 i.e K > 1,then transformer is called step-up transformer.

ii) If N2 < N1 i.e K < 1,then transformer is called step-down transformer.

More details go to:
• electrical4u.com
• electricaleasy.com Multiple Choice Question (MCQ) of Transmission and Distribution page-3:21. ACSR conductor implies A) Anodized Core Smooth Run B) Anode current sinusoidally run C) Aluminium conductor steel reinforced D) All conductors surface treated and realigned.Read more... Multiple Choice Question (MCQ) of Transmission and Distribution page-2:11. In overhead transmission lines the effect of capacitance can be neglected when the length of line is less than A) 80 km B) 100 km C) 160 km D) 200 km.Read more... Multiple Choice Question (MCQ) of Transmission and Distribution page-1:1. Which of the following is not the transmission voltage in India ? A) 400 kV B) 264 kV C) 132 kV D) 66 kV.Read more...