Circuit Breaker is a device which breaks the faulty circuit to protect from damage caused by short-circuit fault current, overload current, earth- fault current in the circuit and after clearing the fault, the load can be easily linked to the circuit by closing the circuit breaker manually or automatically from local or remote operation.
Now, we describe the how circuit breaker operates in a circuit.
The circuit Breaker consists of a fixed contact and sliding contact and a moving contact. The moving contact moves into the sliding contact which is shown in the figure. A handle is attached to a moving contact, which can be manually operated or it can be operated automatically with the help of a mechanism which has a trip coil energized by the secondary current of the current transformer (C.T) which is shown in the figure. Under the normal working condition, the current in the secondary coil of C.T is not sufficient to energize the trip coil fully. But at fault condition, the abnormally high value of current flows in primary of C.T. Resulting high secondary current will flow in the secondary circuit to energize the trip coil so as to release the handle mechanism which opens the circuit breaker. And the circuit breaker disconnects the faulty circuit from the healthy system. The release of the opening mechanism is not instantaneous, but there is always a time lag between the energization of the trip circuit and release mechanism. The release mechanism will pull the moving contact and the resulting motion of the moving contact does not break the circuit immediately because there always exist a certain depth of engagement or between the fixed and moving contact which is shown in the figure.
As soon as the moving contact separates from the fixed contact a heavy arc is produced between them which persist for some time.
A typical voltage and current condition during the opening of the circuit breaker is shown in the figure.
However, In the case of 3 phase A.C circuit Breaker the arc never extinguishes on all the three phases simultaneously because the arc is extinguished only at the instant when the current waveform passes through its zero value and the currents in all the phases cannot pass through their zero values at the same instant. For circuit breaker operation the breaker time is very important because this is a measure of an amount of energy liberated by arcing and the mechanical stresses produced by its components.
The circuit breaker can be classified according to the below table:-
Multiple Choice Question (MCQ) of Electronics page-17:241. Which of the following statement is true? a) The saturation voltage VCF of silicon transistor is more than germanium transistor. b) The saturation voltage VCE for germanium transistor is more than silicon transistor. c) The saturation voltage VCE for silicon transistor is same as that for germanium. d) The saturation voltage VCE for silicon transistor is lower than germanium transistor.
Multiple Choice Question (MCQ) of Electronics page-16:226. Which of the following statement is correct? a) Inner electrons are always present in the semiconductor. b) Bound electrons are always present in the semiconductor. c) Free electrons are always present in the semiconductor. d) Inner and bound electrons are always present in the semiconductor.
Multiple Choice Question (MCQ) of Electronics page-15:211. The materials whose electrical conductivity is usually less than 1 × 106 mho/m are a) Semiconductors b) Conductors c) Insulators d) Alloys
Multiple Choice Question (MCQ) of Electronics page-14:196. In which of the following device the base resistors are not added in the package but added externally? a) UJT b) CUJT c) PUT d) None of the above
Multiple Choice Question (MCQ) of Electronics page-13:181. The conduction in JEFT is always by the a) Majority carriers b) Minority carriers c) Holes d) Electrons e) Holes and electrons simultaneously